Control system of Cormen Training Center - Bystrice nad Pernstejnem, Czech Republic
- Country: Czech Republic
- Name: Control system of Cormen Training Center - Bystrice nad Pernstejnem, Czech Republic
- Implemented by: Tecont s.r.o. and 2AService s.r.o.
- Date: 2012
- Control system: Tecomat Foxtrot
- Software: Reliance
In 2012, company Cormen s.r.o., who is a leading Czech manufacturer of chemical cleaning detergents for industry and households, has built a modern training center. The training center has been placed in additional storey of Cormen administration center, close to the manufacturing plant.
They built more than 700 square meters of flat for trainings of industry cleaning and for examples of Cormen products efficiency.
Training center is fully automated by intelligent electrical installation controlled by system Tecomat Foxtrot from our company. This technology controls and visualize complete lighting system (modern fluorescent tube lights), heating system containing two circuit gas boilers, supplying 25 radiators and floor heating of other part of the building. Heating is controlled according to measurement of outside temperatures and temperatures in rooms. Each room is independent. To change temperature from preset and pre-programmed cycles, they use interior module RCM2-1.
Tecomat Foxtrot here controls as well HVAC system including recuperation and heat pumps for heating of air. Foxtrot is connected with electronic security and fire alarm system Honeywell, including fire alarm sensors. There is also connected access system to Foxtrot. It is used for access to a part of the training center designated for accommodation of trainees. Control of the system is possible by wall touch panels ID-18 and room interior modules RCM2-1.
All processes are visualized and shared in training center control room via HMI SCADA software Reliance 4. Control and monitoring is shared also by web pages and authorized persons may control the system by phone, tablet and other mobile devices.
Control system will be soon expanded by control of a quarter hour maximum, control of heating system for the whole manufacturing plant and warehouse light system including measurement of savings and quantity of illumination.